Shall be a Crown models, gas
fired steam boiler suitable for operation at any pressure from
5-15 psi (34-103 kPa) and to operate on 115 VAC
Boiler shall be mounted in a cabinet base for:
24” (610 mm) wide 200,000 BTU. 36” (914 mm) wide 250,000 or 300,000 BTU.
Polished #4 finish stainless steel cabinet base shall be a modular
design. Shall be equipped with 6” (152 mm) stainless steel legs
with 4 adjustable flanged feet, reinforced stainless steel counter
top, and hinged doors with magnetic latches. All piping shall be
confined within cabinet.
Unit shall come standard with automatic water level control,
pressure gauge, water gauge glass, pressure control with
secondary safety pressure control, safety relief valve, split water
line, automatic boiler blow-down, CSD-1 boiler controls, steam
take off kit, nickel plating, and electronic ignition.
Thermostatically controlled cold water shall automatically
condensate exhausted steam into water before releasing it to